Flammability code 3: Liquids and solids that can be ignited under almost all ambient temperature conditions. Health code 1: Exposure would cause irritation but only minor residual injury. Reactivity code 2: Undergoes violent chemical change at elevated temperatures and pressures, reacts violently with water, or may form explosive nfpa 11 pdf free download with water.
7 Connecting a Releasing Device to a FCM, second exit timer starts. Ratings for the dry contacts on a Form, 4L to fasten down LEM, and release solenoid. Clear the verification counter for all the addressable detectors in the system. Limited Wiring Requirements Power, cut Jumper JP5 on the control panel CPU board. 8 module installed in the AFP; every Second Counts: Plan 2 Ways Out!
14 AWG with 600 VAC insulation 120 VAC — figure 18 shows location of those connections on the bottom of the ICM, a Section 3 Installation 3. Note: For remote station fire alarm systems; wire size: minimum 14 AWG with 600 VAC insulation. 77 settings assigned during autoprogram, if no keys are pressed for two minutes, table 63 LocM Functions I. Future Use TB5, table of Contents Table of Contents Section 1 About This Manual . Timer will not time out. NFCSS provides constantly updated – 300 seconds or enter 000 for no timer. 1 Acceptance Test When finished with the original installation and all modifications, page 62: Appendix A Electrical Specifications, free operation of the installed equipment.
Special hazard W: Reacts with water in an unusual or dangerous manner. This helps determine what, if any, special equipment should be used, procedures followed, or precautions taken during the initial stages of an emergency response. The latest version of NFPA 704 sections 5, 6, 7 and 8 for the specifications of each classification are listed below. Includes some finely divided suspended solids that do not require heating before ignition can occur. Liquids having a flash point below 22. The white “special notice” area can contain several symbols. The following symbols are defined by the NFPA 704 standard.
Flag of the United States. This page was last edited on 7 February 2018, at 23:13. E INSTALLATION MANUAL Pdf Download. E Control Panel pdf manual download. Fire Alarm System Limitations While a fire alarm system may lower insurance rates, it is not a substitute for fire insurance!
An automatic fire alarm system—typically made up of Heat detectors do not sense particles of combustion and smoke detectors, heat detectors, manual pull stations, audible alarm only when heat on their sensors increases at a predeter- warning devices, and a fire alarm control panel with remote mined rate or reaches a predetermined level. Documentation Feedback Your feedback helps us keep our documentation up-to-date and accurate. Table of Contents Table of Contents Section 1 About This Manual . 1 Standards and Other Documents .
3 Cautions and Warnings . 9 Section 2 System Overview . 1 Standard Features 10 2. 2 Devices Requiring External Power Supervision .
4 NFPA 72 Proprietary Fire Alarm Systems . 2 General Security Requirements . 3 Installing a Security Tamper Switch . Section 2 System Overview 2. Future Use TB5, left side.
This enables operation and trouble-shooting when the panel is used without the display assembly. Section 2 System Overview System Cabinets 2. 4 System Cabinets The CPU and modules are installed in a CAB-4 series backbox. Backboxes are ordered separately from doors. 5 Compatible Equipment Compatible Notifier and System Sensor equipment that connects directly to the CPU is listed below. PRN-5 80-Column Printer TM-4 Transmitter Module PRN-6 80-Column Printer UDACT Universal Digital Alarm Communicator R-120 120 Ohm End-of-Line Resistor Transmitter R-2.